Water delivery systems – legislation
The Public Health and Wellbeing Regulations 2019 require certain premises with water delivery systems to manage the risks associated with Legionella.
Regulation 82 of the Regulations requires that the responsible person must take all reasonable steps to manage the risks of Legionella in water delivery systems in certain premises.
The 'certain premises' that the regulations apply to are:
- where residential aged care services are provided; and
- where health services are provided (but does not include health services provided at a day procedure centre);
- that are prisons;
- where impatient forensic mental health services are provided by the Victorian Institute of Forensic Mental Health, and;
- where commercial vehicle washers are operated.
The responsible person is any person who owns, manages, or controls the water delivery system.
The regulations are available at the Victorian legislation and parliamentary documents website.
Information about responding to a detection of Legionella in a water delivery system is available at Responding to a Legionella Detection.
Water delivery systems – Legionella risks
Legionella has been detected in water delivery systems associated with showers and ice machines in hospitals and aged care facilities in Victoria. In addition, in 2008, a car wash facility was linked to seven cases of Legionnaires’ disease.
Legionella is an organism that is ever-present in the environment and found in very low concentrations in the potable water supply. In the right environment, however, the Legionella bacteria are able to multiply and pose significant risks to the health of individuals exposed to the bacteria.
The risk of Legionella growth increases in water delivery systems that store water at temperatures between 20 °C and 60 °C. In addition, the risks of Legionella growth in commercial car washes are increased when rubber hosing is used and when there is an absence of a biocide.
People may contract Legionnaires’ disease if they are exposed to small droplets containing the bacteria, like those produced by high pressure hoses or showers.
Water delivery systems – managing the risks of Legionella
In order to comply with the Regulations and reduce the risk of Legionella in your warm water system, the department recommends that a Legionella risk management plan be developed for your water delivery system in line with Enhealth Guidelines for Legionella Control in Health and Aged Care Facilities. A risk management template has also been developed to assist with the process.
These Guidelines are designed to be used throughout Australia and New Zealand and do not incorporate the Victorian legislative requirements.
Assessments of water delivery systems should not be restricted to showers systems and should include any system where the water in the system is at temperatures between 20°C and 60°C combined with the potential for a person to be exposed to respirable sized water droplets from the system.
Commercial car washes – suggestions to manage the risks associated with Legionella
To manage the risks associated with Legionella in commercial car washes, the department recommends that the following be considered:
- not storing water at temperatures between 20 °C and 60 °C
- replacing warm water storage with instantaneous units
- replacing rubber hosing with poly tubing, metal tubing, or copper tubing
- regularly disinfecting the system with a chlorine-based disinfectant.
You can also obtain further information from the Australian Car Wash Association.